- covering Sussex and surrounding areas. 01444 244 344
A fire-resisting door or fire door is provided to resist the passage of fire, smoke and heat for a significant period, usually 30 minutes or 60 minutes so that the occupants of a building can safely evacuate the building. In holding back fire and smoke, escape routes are maintained and fire spread within the building is resisted. Any door in a fire resisting wall or partition must be a fire door.
Fire doors other than those to locked cupboards and service cupboards normally need to be self-closing. Self-closing devices should be of a type, which can not be easily removed or tampered with, which will completely close a door, and overcome the resistance of a latch fitted, from fully open or partially open position. These should be to BS EN 1154.
An intumescent seal should be fitted across the head of the door and down the sides of the door. Alternatively the seal can be fitted in the door frame. There is normally a gap of 2-4mm between door and frame. Hinges must be capable of taking the increased weight of the door.
Fire-resisting doors need to be hung with the correct number, size and quality of hinges. Normally, a minimum of three 102mm hinges are needed and these should be to BS EN 1935.
Door Assist, The Fire and Security Shop, 1 Eastern Rd, Haywards Heath, West Sussex. RH16 3NG
Registered Office: 63 High Street, Hurstpierpoint, West Sussex, BN6 9RE. Company Registration No. 8610060 registered in England & Wales
The Fire & Security Centre
1 Eastern Road
If you have any queries or wish to make an appointment, please contact us:
01444 244 344
Or use our contact form.